This circuit breaker wiring diagram illustrates installing a 30 amp circuit breaker for a 240 volt circuit. The 10/3 cable for this circuit has 3 conductors and no ground. A 30 amp circuit like this is usually found in water heater circuits and older installations for clothes dryers and kitchen ranges. For a new installation of a kitchen range, use the diagram below for a 50amp circuit.
This diagram illustrates wiring for a circuit breaker with a built-in ground fault circuit interrupter. This 20 amp ground fault interrupter breaker is a form of gfci that can be installed at the circuit source. This kind of circuit is used for dishwashers, whirlpool spas and other locations where water contact is likely.
This diagram shows the wiring for a new receptacle added from a light switch. The switch must have an always-hot wire for the source and a neutral wire must be present for the return path. The hot source is spliced with a pigtail back to the switch, and to a new 2-wire cable running to the new outlet. The neutral is spliced in the switch box to both the existing light, and the cable to the new receptacle.
To add a new outlet to a group of receptacles already in place, splice the new wires to one set of wires on one of the existing receptacles. In this diagram each receptacle is wired to the next using the terminals to pass the voltage along. To provide voltage to a new receptacle, remove the wires from one set of terminals on the existing outlet and splice in the new wires and a pigtail back to each terminal.