This circuit breaker wiring diagram illustrates installing a 30 amp circuit breaker for a 240 volt circuit. The 10/3 cable for this circuit has 3 conductors and no ground. A 30 amp circuit like this is usually found in water heater circuits and older installations for clothes dryers and kitchen ranges. For a new installation of a kitchen range, use the diagram below for a 50amp circuit.
An isolated-ground receptacle makes use of an extra wire for a separate ground in the circuit. This is the red wire in the 14/3 cable used here which is marked and connected to the grounding terminal on the receptacle. The other cable wires are connected as with any other circuit except for the ground wire. The bare copper ground wire is NOT connected to the receptacle, instead it is connected to the grounding terminal inside the electrical box where the receptacle is housed.
This circuit breaker wiring diagram illustrates installing a 20 amp circuit breaker for a 240 volt circuit. The 12/2 gauge cable for this circuit includes 2 conductors and 1 ground. A dedicated 20 amp circuit like this is used for heavy household appliances like an air conditioners.
The always-hot wire from the receptacle is spliced to the black wire on the fixture cable, and to a pigtail that connects back to the hot terminal on the receptacle. At the light fixture box, the black is spliced to the black from the switch cable. At the switch box the black wire is connected to the bottom terminal on the new switch.