Here a receptacle is added to a 3 way light circuit before the first switch. It is not controlled with the switches but is instead always hot. The source hot, neutral and ground are spliced to a 2-wire cable that runs to the new outlet. The 3 way switches and light are then wired in the usual way with the common on SW2 spliced to the source hot and the light hot wired to the common on SW1.
Here 3-wire cable serves a split receptacle. The bottom half of the receptacle is controlled by a switch and the top half is always-hot.
If you’re installing a new doorbell, a remote controlled device makes for the simplest installation and doesn’t require any of the circuitry illustrated on this page. All that’s required is to mount the button near an exterior door and the chimes in a convenient, central location inside the house. No need to run wires or splice into household circuits, fresh batteries are all that’s required.
A special isolated-ground receptacle is require for this circuit and can be identified by the orange color and a small triangle imprinted on the face. When connecting the wires, the isolated ground wire (the red wire pictured here) is marked with green tape or paint on each end and connected to the grounding bar in the service panel, and to the grounding terminal on the receptacle.